Over deze norm
1.1 This practice provides information on apparatus, safety, pre-test preparation and procedures for conducting field tests of polyethylene pressure piping systems after installation using gaseous media such as unodorized inert non-toxic gas or air, and applying pressure to determine if leaks exist in the system (pneumatic leak testing). This practice applies only to testing to discover leakage. Testing for other purposes such as testing to establish operating pressure is beyond the scope of this practice.
1.2 This practice does not address leak testing using pressurized liquids (hydrostatic testing). For field leak testing using pressurized liquids, see Practice F2164.
1.3 Leak testing with pressurized gaseous media shall be used only if one of the following conditions exists:
1.3.1 The piping system is so designed that it cannot be filled with a liquid, or
1.3.2 The piping system service cannot tolerate traces of liquid testing media.
1.4 Where hydrostatic testing is specified in contract documents or by the authority having jurisdiction, pressurized gaseous media (pneumatic) testing shall not be substituted without the express consent and authorization of the authority having jurisdiction.
1.5 Some manufacturers prohibit or restrict pressurized gaseous media testing of their products. Contact component manufacturers for information about testing with gaseous media under pressure. Where the manufacturer of a test section component prohibits or restricts pressurized gaseous media testing, pressurized gaseous media (pneumatic) testing shall not be used without the express consent and authorization of the authority having jurisdiction and the component manufacturer.
Note 1—Components that are not suitable for testing with gaseous media may not be suitable for service with pressurized gaseous media.
1.6 This practice does not apply to leak testing of non-pressure, negative pressure (vacuum), or non-PE piping systems. For field acceptance testing of plastic gravity flow sewer lines, see Test Method F1417.
1.7 This practice does not apply to fuel gas piping systems that extend from the point of delivery to the appliance connections. For other than undiluted liquefied petroleum gas (LP-Gas) systems, the point of delivery shall be considered to be the outlet of the service meter assembly or the outlet of the service regulator or service shutoff valve where no meter is provided. For undiluted LP-Gas, the point of delivery shall be considered to be the outlet of the final pressure regulator, exclusive of line gas regulators, in the system. Testing for these systems can be found in NFPA 54 / ANSI Z223.1. This practice does not apply to LP-Gas systems covered under NFPA 58.
1.8 This practice is intended for use with polyethylene pressure piping that conveys gaseous media under pressure (compressed gas) if the owner or operator or installer of the line does not have an established leak testing procedure that is acceptable to the authority having jurisdiction.
1.9 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard. Numbered notes and information in parentheses in the text of the practice are non-mandatory information. Table notes are mandatory information.
1.10 Warning—Failure during a pressure leak test can be extremely violent and dangerous especially where a compressed gaseous media is used. In a compressed gaseous media test, energy is applied to compress the gaseous media in addition to pressurizing the system. If failure occurs, both energies can be suddenly released and can be extremely violent compared to failure during leak testing with an incompressible liquid testing media.
Note 2—To illustrate the violent hazard of failure, assume a 5 Hp compressor is used to raise the test section to test pressure and that it takes 1 h to achieve test pressure. If sudden rupture occurs, energy release may occur in 2 s. Therefore, the horsepower of the energy release would be 5 HP × 1 h × 3600 sec/h / 2 s = 9,000 Hp. Further, if diameter is doubled, energy release is four times greater. For an example test section that is twice the diameter, energy release would be 36,000 Hp.
1.11 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Additional safety information is presented in Section 7 and throughout this practice.
|Engelse titel||Standard Practice for Field Leak Testing of Polyethylene (PE) Pressure Piping Systems Using Gaseous Media Under Pressure (Pneumatic Leak Testing)|