Over deze norm
1.1 These test methods cover three electrical tests on plastic guards and assembled guard systems. They are:
1.1.1 Method A—Withstand voltage proof test,
1.1.2 Method B—Flashover voltage, and
1.1.3 Method C—Leakage current.
1.1.4 This specification covers plastic guard equipment and guard systems used by workers for temporary insulation on electric power circuits.
1.1.5 Plastic guard equipment covered by this specification is rated for momentary, or brush contact only. Maximum-use voltages are covered in Table 1 and Table 2.
1.2 These test methods cover, but are not limited to, the following typical guards:
1.2.1 Conductor Guards and Connecting Covers as follows:
184.108.40.206 Line guards,
220.127.116.11 Line guard connectors,
18.104.22.168 Insulator covers,
22.214.171.124 Dead-end covers,
126.96.36.199 Bus guards, and
188.8.131.52 Bus “T” guards.
1.2.2 Structure and Apparatus Covers as follows:
184.108.40.206 Pole guards,
220.127.116.11 Ridge pin covers,
18.104.22.168 Switch blade covers,
22.214.171.124 Arm guards,
126.96.36.199 Cutout covers,
188.8.131.52 Structural barriers, and
184.108.40.206 Cross arm guard.
1.3 It is common practice for the user of this equipment to prepare instructions for the correct use and maintenance.
1.4 The use and maintenance of this equipment is beyond the scope of these test methods.
1.5 This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
1.6 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
|Nederlandse titel||Standard Test Methods and Specifications for Electrically Insulating Plastic Guard Equipment for Protection of Workers|
|Engelse titel||Standard Test Methods and Specifications for Electrically Insulating Plastic Guard Equipment for Protection of Workers|