Over deze norm
|Commissie||Installatievoorschriften, lage spanning|
Is intended to provide for a satisfactory life of conductor and insulation subjected for the thermal effects of carrying current for sustained periods in normal service. Contains a schedule of installation methods. Gives the current-carrying capacities for nominal cross-sectional areas of conductor from 1,0 mm2 to 300 mm2 depending of the different methods of installation. relates for the time being only to non-armoured cables having nominal voltage not exceeding 0,6/ 1 kV.
|Engelse titel||Electrical installations of buildings. Part 5 : Selection and erection of electrical equipment. Chapter 52: Wiring systems - Section 523 - Current-carrying capacities|