Over deze norm
This European Standard applies to shell boilers with volumes in excess of 2 litres for the generation of steam and/or hot water at an allowable pressure greater than 0,5 bar and with a temperature in excess of 110 °C. The purpose of this European Standard is to ensure that the hazards associated with the operation of shell boilers are reduced to a minimum and that adequate protection is provided to contain the hazards that still prevail when the shell boiler is put into service. This protection will be achieved by the proper application of the design, manufacturing, testing and inspection methods and techniques incorporated in the various parts of this European Standard. Where appropriate, adequate warning of residual hazards and the potential for misuse are given in the training and operating instructions and local to the equipment concerned (see EN 12953-7 and EN 12953-8). This European Standard specifies requirements for both directly fired and electrically heated boilers including low pressure boilers (LPB, see 3.7) as well as for waste-heat boilers with a gas-side pressure not exceeding 0,5 bar1) of cylindrical design, constructed from carbon or carbon manganese steels by fusion welding and a design pressure not exceeding 40 bar. The boilers covered by this European Standard are intended for land use for providing steam or hot water (typical examples are shown in Figures 3.1 to 3.6). Where a particular boiler is a combination of shell and water-tube design then the water-tube standard series EN 12952 is used in addition to this European Standard. One such example of this combination is shown in Figure 3.3. This European Standard applies to the generator, from the feed-water inlet connection to the steam outlet connection and to all other connections, including the valves and steam and water fittings. If welded ends are used, the requirements specified herein begin or end at the weld where flanges, if used, would have been fitted. For Low Pressure Boilers (LPB) less stringent requirements concerning design and calculation are acceptable. Details are defined in the respective clauses.
|Nederlandse titel||Vlampijpketels - Deel 1: Algemeen|
|Engelse titel||Shell boilers - Part 1: General|
|Vervangen door||Normatieve verwijzingen||