Over deze norm
This European Standard establishes the requirement for the design and use of vitreous enamel coated bolted cylindrical steel tanks for the storage and treatment of municipal and industrial effluent. This European Standard applies to the design of the tank and any associated roof and gives guidance on the requirements for the design of the foundation. This European Standard applies where: a) the tank is cylindrical and symmetrical on plan and is mounted on a load-bearing base substantially at or above ground level; b) the multiple of the tank diameter in meters and the wall height in meters has a value within the range 5 to 500; c) the stored material is a liquid; the stored material may be undergoing treatment as part of a municipal or industrial effluent treatment process; d) the internal pressure above the liquid does not exceed + 50 kPa or -10 kPa; e) the walls of the tank are vertical; f) the floor of the tank is substantially flat at its intersection with the wall; the floor of the tank may have a rise or fall built in to allow complete emptying of the tank contents; such fall or rise should not exceed one hundredth of the tank diameter; g) there is negligible inertial and impact load due to tank filling; h) the minimum thickness of the tank shell is 1;5mm; i) the material used for the manufacture of the steel sheets is carbon steel; (tanks constructed of sheets made from aluminum or stainless steel are outside the scope of this Standard), j) the temperature of the steels used in the construction is within the range - 50 ºC ± 100 ºC under all operating conditions. This European Standard also gives details of procedures to be followed during site installation and for inspection and maintenance of the installed tank.
|Nederlandse titel||Email - Ontwerp van met email beklede stalen tanks voor de opslag of behandeling van water of gemeentelijk of industrieel afval|
|Engelse titel||Vitreous en porcelain enamels - Design of vitreous enamel coated bolted steel tanks for the storage or treatment of water or municipal or industrial effluents.|