Over deze norm
This document is applicable to water based surface heating and cooling systems in buildings as defined in part 1 of this standard. Physiological limitations are taken into account when specifying the maximum and minimum surface temperature. The design is based on performance characteristic curves and limit curves calculated in accordance with part 1 of this standard. Design considerations for heating and cooling systems are given.
|Nederlandse titel||Verwarmingssystemen in gebouwen - Ontwerp van ingebouwde oppervlakteverwarmings- en koelsystemen - Deel 2: Ontwerp, dimensionering en installatie|
|Engelse titel||Heating systems in buildings - Design of embedded water based surface heating and cooling systems - Part 2: Design, dimensioning and installation|