Over deze norm
This document is applicable to water based surface heating and cooling systems in residential, commercial and industrial buildings. The methods apply to systems integrated into the wall, floor or ceiling construction without any open air gaps. The methods do not apply to heated or chilled ceiling panels or beams. This standard is part 3 of a series of standards: - Part 1: Steady-state calculation methods for determination of the heating and cooling capacity; - Part 2: Method for design, dimensioning and installation; - Part 3:Optimizing for use of renewable energy sources. The aim of the present Standard is to give a guide for the design for use of renewable energy sources and for the use of Thermo-Active-Building-Systems (TABS). The tool allows calculation of peak cooling capacity of a thermo-active system, based on heat gains (solar, internal loads, ventilation). This method also allows calculation of the energy demand on the water side (system) to be used for sizing of the cooling system, like chiller, fluid flow rate, etc. Steady state heating capacity is calculated according to method B or E, ref. Part 1 of this series of standards. The present standard requires input from the following standards: prEN 15377-1, prEN wi 16, prEN wi 17 and prEN wi 031 (see 2). The present standard provides input data to the following standards: prEN wi 12 (Calculation of room temperatures and of load and energy for buildings with room conditioning systems) and prEN wi 28 (Thermal performance of buildings - Calculation of internal temperatures of a room in summer without mechanical cooling - simplified methods).
|Nederlandse titel||Verwarmingssystemen in gebouwen - Ontwerp van ingebouwde oppervlakteverwarmings- en koelsystemen - Deel 3: Optimaliseren van het gebruik van duurzame energie|
|Engelse titel||Heating systems in buildings - Design of embedded water based surface heating and cooling systems - Part 3: Optimizing for use of renewable energy sources|
|Vervangen door||Normatieve verwijzingen||