Over deze norm
|Commissie||Ventilatie en luchtdoorlatendheid van gebouwen|
This document gives guidance for system designers, installers, commissioners and maintenance teams on the incorporation of protective measures for air distribution system within buildings to prevent the initiation and the spread of fire, smoke and other by-products of combustion. It defines those performance and characteristics (mandatory or optional) which shall be required to deal with fire precautions for air distribution systems in buildings. It is recommended to use products according to EN standards. It is recommended to estimate the behaviour of the whole ventilation system based on the characteristics of components. If there are no standards available, analytical method or local regulations should be used. This document applies to all ventilation systems (except systems only dedicated to smoke exhaust and those which are described in CR 12101-5) including plant rooms, shafts and penetrations, and following components/products used in the system: - inlet/outlet louvres; - fans not submitted/submitted to the smoke; - air control dampers; - ducts; - fire control dampers; - air terminal devices; - air transfer devices; - anchors and supports; - duct fittings; - control devices; - cables and connections; - air handling units; - air filters - sound attenuators; All the products covered by this standard shall conform to European directives, for example : Low voltage Directive, EMC Directives, Construction Product Directive.
|Nederlandse titel||Ventilatie van gebouwen - Voorzorgsmaatregelen tegen brand voor luchtverdeelsystemen in gebouwen|
|Engelse titel||Ventilation for buildings - Fire precautions for air distribution systems in buildings|