Over deze norm
||CV- en warmwatertoestellen
This European Standard specifies the requirements and test methods for the construction, the safety and the rational energy usage for gas-fired standard and low temperature central heating boilers equipped with a forced draught burner. These boilers comprise a boiler body and a forced draught gas burner brought together at the producer's assembly facility, the whole being designed and marketed as a complete boiler. This standard does not apply to the case of the assembly of a boiler body and a forced draught gas burner designed and marketed separately. In this case, EN 303-3 applies. This European Standard applies to type B23 boilers with a nominal heat output not exceeding 1000 kW with a water temperature at normal operation not exceeding 105 Â°C and with a maximum water-side operating pressure not exceeding 8 bar. This European Standard does not contain all the necessary requirements for: - condensing boilers and combination boilers; - boilers intended to be installed in the open; - boilers permanently fitted with more than one flue outlet; - boilers intended to be connected to a common flue having mechanical extraction; - boilers equipped with several combustion chambers. This European Standard does not apply to living-space dedicated boilers (see 3.6). This European Standard only covers type testing.
||Verwarmingsketels - Deel 7: Met gas gestookte centrale-verwarmingsketels met een ventilatorbrander met nominale belasting tot 1000 kW
||Heating boilers - Part 7: Gas-fired central heating boilers equipped with a forced draught burner of nominal heat output not exceeding 1000 kW
- 2009/142/EG, Gastoestellen